TYPE Accessory HOUSING Handheld POWER SUPPLY Bus-powered Others TYPE Test unit HOUSING Handheld POWER SUPPLY Bus-powered MAIN CHARACTERISTICS Test unit for monitoring and activating smart-house signals
Test Unit BGT-TEST-SP Portable test unit Monitoring of smart-house channel status LCD-display 12-key tactile keyboard Supplied by smart-house Transmission latch Dual-group reading Analog BCD reading Split I/O channel reading PRODUCT SPECIFICATIONS Output smart-house Connection3 mm Jack socket Display 2 x 16 characters TypeLCD Height of dots5 mm KeyboardTactile keys No. of keys12 Channel keys 1-8 Command keys« ↑ » « ↓ » (scroll up/down) « MODE », « ENTER » Cable 1BGT-TEST-SP to smart-house BGT-TEST-SP connector 3 mm Jack plug smart-house connector 2 mini grips SignalRed CommonBlack Cable 2BGT-TEST-SP to Chip module BGT-TEST-SP connector 3 mm Jack plug smart-house connector 1 6/6 modular plug GENERAL SPECIFICATIONS Environment Degree of protectionIP 40 Pollution degree 3(IEC 60664) Operating temperature 0° to +50°C (+32° to +122°F) Storage temperature -20° to +60°C (-4° to +140°F) Humidity (non-condensing)20 to 80% Mechanical resistance Shock 15 G (11 ms) Vibration 2 G (6 to 55 Hz) Dimensions (l x w x d) 145 x 90 x 28 mm Material ABS, grey Weight 250 g SUPPLY SPECIFICATIONS Power supply Supplied by smart-house Reverse-polarity protectionYes Rated operational current < 4.0 mA MODE OF OPERATION TYPE SELECTION Supply Ordering no. Supplied by smart-houseBGT-TEST-SP ADDITIONAL INFORMATION 128-channel portable transmit- ter/receiver unit supplied by smart-house. The BGT-TEST-SP can be used anywhere along the two wires to monitor and control the status of smart-house chan- nels. Thisunitis highly recom- mended for start-up and mainte- nance work on smart-house sys- tems. The BGT-TEST-SP can operate in 6 different modes: Digital 1 group Digital 2 groups Edit Tx-latch Analog BCD Split I/O Sensor Calibration Warning: Do not plug or unplug the Jack connector when the BGT- TEST-SP is connected to smart- house. This will cause a short-cir- cuit of the two wires. Note: If the smart-house carrier is missing, the display will not turn on. Scope of supply 1 x Test unit BGT-TEST-SP 1 x Cable 1 (mini grips) BGT-TEST-SP - GRIP - CAB 1 x Cable 2BGT-TEST-SP - ASIC - CAB WIRING DIAGRAM D+ D- Supplied by smart-house Specifications are subject to change without notice (20.11.2007) - A product of the CARLO GAVAZZI Group
All ratings we receive from the items we offer are real and verified. A small gesture, but a lot of value. That's why we thank you for that minute you invest in leaving us your opinion and qualification about the products, because it helps us to continue improving and to offer you a service of even higher quality.