For use with
Type E starters do not need an upstream protective device.
For use in Canada, the PKZM0/PKZM4 must be fitted with an AK-PKZ0.
Service factor (SF)
Set value Ir on the current scale, depending on the load factor
SF = 1.15 ￫ Ir = 1 x In mot
SF = 1 ￫ Ir = 0.9 x In mot
For three-phase commoning link, protected against accidental contact, Ue = 690 V, Iu = 60 A
For conductor cross-sections:
2.5 - 25 mm2 stranded
2.5 - 16 mm2 Flexible with ferrule
AWG 14 - 6
For surface-mounting type-E starters.