Remote Control BDF-WLS3 smart-house transmitter for building automation applications 3 individually programmable push-buttons 3 V battery supply (CR2032) Channel programming using BGP-COD-BAT Range up to 40 m in open air Battery life: up to 5 years at normal use INPUT SPECIFICATIONS Wireless push-button Transmission frequency868 MHz SUPPLY SPECIFICATIONS Power supplyBattery: CR2032 3V GENERAL SPECIFICATIONS Channel codingVia BGP-COD-BAT and special cable: GAP-TPH-CAB. Following the installation, the program- ming can be changed by removing the thin cover between the push-buttons and using the supplied adapter for the GAP-TPH-CAB cable. Battery change It is possible to change battery if the battery voltage is low. Use a sharp object to separate the two plastic parts. Replace the battery and reassemble the plastic parts by pressing them together. Out 1-3Push-button 1-3 HousingCompact Environment Protection degree IP 20 Pollution degree 3 (IEC 60664) Operating temperature 0-50°C/32-122°F Storage temperature -20-70°C/-4-158°F Humidity (non-condensing)20 - 80% Weight30 g – battery included MODE OF OPERATION The BDF-WLS3 remote control is designed for base unit BH4-WBUx- 230 and will only function with this unit. The remote control is programmed using aBGP-COD-BAT (see data sheet for this unit). The communication between BDF- WLS3 and the BH4-WBUx-230 base is established in the following way: - Push the “Mode” button on the BH4-WBUx-230 base until the red LED indicates association. - Push the push-button on the BDF- WLS3 remote control module that youwanttoassociatewiththe BH4-WBUx-230 base. Once the association is complete, the LED will light up briefly (approx. 1 second). If the association fails, e.g. because the range is exceeded, the LED in the remote control module will light up simultaneously for approx. 500 ms. This also occurs if, under normal circumstances, it is not possibletoestablishconnection between the BH4-WBUx-230 base and the BDF-WLS3 remote control modules. It is possible to disable the commu- nication between the BH4-WBUx- 230 base and all the modules with which it is associated. - Push the “Mode” button on the BH4-WBUx-230 base until the red “Disable” LED is lit. This means that there is no connec- tion between the BH4-WBUx-230 base and its associations. To reestablish the connection, push “Mode” until neither “Associate” or “Deactivate” are lit. Under normal circumstances, the “Supply” and “smart-house” LEDs willbelitcontinuously,whereas the LED for “Communication” only blinks briefly when you push an associated BDF-WLS3 remote con- trol. The LED always lights up when you push a button. The LED indication provides confir- mation that the communication is successful. DIMENSIONS (mm) 12 45 TYPE SELECTION Supply Ordering no Battery BDF-WLS3 2 3 COMMUNICATION EXAMPLE 1 smart-house bus 2 3 1 PUSH BOTTON/LED ALLOCATION 1 2BH8-CTRLZx-xxx 1 2BH4-WBUA-230 2 3 1 LED IO1 Pushbutton 1 IO2 Pushbutton 2 IO3 Pushbutton 3 IO5 LED IO6 LED IO7 LED Power smart-house RF Associate Disable Mode Specifications are subject to change without notice (07.11.2007) - A product of the CARLO GAVAZZI Group
All ratings we receive from the items we offer are real and verified. A small gesture, but a lot of value. That's why we thank you for that minute you invest in leaving us your opinion and qualification about the products, because it helps us to continue improving and to offer you a service of even higher quality.