|Undervoltage release for use with delay unit UVU|
|Combination of separate delay unit and special releases.|
For use with emergency switching off devices in conjunction with Emergency switching off button.
not UL/CSA approved
Special releases for combining with separate delay time.
UVU-NZM delay unit is additionally required.
Cannot be installed simultaneously with separate NZM...-XHIV early-make auxiliary contact or NZM...-XA... shunt release.
Cannot be used in conjunction with NZM...-XR... remote operator.
Early make of auxiliary contact on switching on and off (manual operation): approx. 20 ms.
|with 3 m loose connection cable instead of screw termination|
|with two separate early-make auxiliary contacts|
For use with