Wireless Base Unit with External Antenna BH4-WBUA-230 smart-house transceiver for building automation applications Easy to install in both old and new installations Unlimited number of connected wireless switches BH4-WBUA-230 DIN-rail mounting Range up to 100 m in open air Easy to operate External antenna SUPPLY SPECIFICATIONS Power supply AC types Overvoltage cat. III (IEC60664) Rated operational voltage through term. 21 & 22 230 230 VAC, ±15% Frequency 45 to 65 Hz Voltage drop-out 40 ms Rated operational power Typ. 3 VA Power dissipation 3 W Rated impulse voltage 230 4 kV Dielectric voltage Supply – smart-house4 kVAC (rms) GENERAL SPECIFICATIONS Power ON DelayTyp. 2 s Indication of Power ON Green LED smart-house signal Yellow LED Wireless communication ON Green LED AssociationRed LED Disable RF Red LED Environment Protection degree IP 20 Pollution degree 3 (IEC 60664) Operating temperature -20°C to +50°C (-4° to + 122°F) Storage temperature -50°C to +85°C (-58° to +185°F) Humidity (non-condensing) 20 to 80% Mechanical resistance Shock15 G (11 ms) Vibration 2 G (6 to 55 Hz) Dimensions72 x 77 x 70 mm Material (see “Techical information”) H4 housing Antenna The ANT 1 is used, but not includ- edWeight 250 g Special conditionsIf the wireless base unit is placed in a metal cabinet or another kind of metal installation, it might reduce its range. Therefore the antenna must be placed outside the cabinet or in open areas. MODE OF OPERATION The wireless Bxx-WLS4 switches are programmed as standard Fuga/Opus switches (but with no channel coding for (I/O 5-8, as the leds automatically follow the but- tons). The communication between the Bxx-WLS4 wireless switch and the BH4-WBUA-230 base is estab- lished in the following way: The used smart-house adresses of wireless devices are all pro- grammed at the wireless device. The only "special" interaction regarding wireless devices is the association process. This process makes sure that your wireless devices are not disturbed by the devices of your neighbour. To associate a device with the base: 1) Press the "mode" button on the base. The association led lights up. 2) Press a button on the wireless device to be associated. - All leds on the device will light up for about 1 second. 3) Press the "mode" button on the base unit until both Association and disabled-leds are off. This indicates "normal operation". If the connection from a wireless device fails, alle leds will flash briefly after trying to communicate with the base unit three times. If a device associated with base A is in sight of bases A and B and you want to reassociate the device with base B, do the following: 1) Select the "Disabled" mode on base A. 2) Select the "Associate" mode on base B. 3) Press a button on the wireless device to be associated. - All leds on the device will light up for about onesecond. 4) Press the "mode" button on both base units until both Association and disabled-leds are off. This indicates "normal operation". The LEDs: The "Power" LED indicates that the unit is powered. (230Vac) The "smart-house OK" LED indi- cates detected smart-house signal. The "RF" LED indicates received wireless communication directed to this base. The "Associate" LED indicates the association mode. The "Disabled" LED indicates that the base ignores any wireless com- munications. DIMENSIONS (mm) INPUT SPECIFICATIONS Wireless communication at 868 MHz smart-house bus I1I3 1 2BH8-CTRLZx-xxx 1 2BH4-WBUA-230 I2I4 BOW-WLS4 Mode Power smart-house RF Associate Disable 868 MHz I1 I3 I2I4 BFW-WLS4 Specifications are subject to change without notice (16.01.2009) - A product of the CARLO GAVAZZI Group
All ratings we receive from the items we offer are real and verified. A small gesture, but a lot of value. That's why we thank you for that minute you invest in leaving us your opinion and qualification about the products, because it helps us to continue improving and to offer you a service of even higher quality.