Remote Control BDF-WLS8 smart-house transmitter for building automation applications 8 individually programmable push-buttons 2 x AAA battery used as supply Channel programming using BGP-COD-BAT Range up to 40 m in open air INPUT SPECIFICATIONS Wireless push-button Transmission frequency868 MHz SUPPLY SPECIFICATIONS Power supplyBattery: 2 x AAA (LR03) GENERAL SPECIFICATIONS Channel codingVia BGP-COD-BAT and special cable: GAP-TPH-CAB. Following the installation, the pro- gramming can be changed by remov- ing the lid on the bottom of the remote control and using the supplied adapter for the GAP-TPH-CAB cable. Battery change If LED is not responding by pressing the pushbuttons, the battery voltage could be low. Replace the battery and reassemble the plastic parts. Out 1-8Push-button 1-8 HousingCompact Current consumption Activated< 1 mA Non activated< 10 µA Environment Protection degree IP 20 Pollution degree 3 (IEC 60664) Operating temperature 0-50°C/32-122°F Storage temperature -20-70°C/-4-158°F Humidity (non-condensing)20 - 80% Weight30 g – battery excluded MODE OF OPERATION The BDF-WLS8 remote control is designed for base unit BH4-WBUx- 230 and will only function with this unit. The remote control is programmed using a BGP-COD-BAT (see data sheet for this unit). The communication between BDF- WLS8 and the BH4-WBUx-230 base is established in the following way: - Push the “Mode” button on the BH4-WBUx-230 base until the red LED indicates association. - Push the push-button on the BDF- WLS8 remote control module that you want to associate with the BH4-WBUx-230 base. Once the association is complete, the LED will light up briefly (approx. 1 second). If the association fails, e.g. because the range is exceeded, the LED in the remote control module will light up simultaneously for approx. 500 ms. This also occurs if, under normal circumstances, it is not pos- sible to establish connection between the BH4-WBUx-230 base and the BDF-WLS8 remote control modules. It is possible to disable the commu- nication between the BH4-WBUx- 230 base and all the modules with which it is associated. - Push the “Mode” button on the BH4-WBUx-230 base until the red “Disable” LED is lit. This means that there is no connec- tion between the BH4-WBUx-230 base and its associations. To reestablish the connection, push “Mode” until neither “Associate” or “Deactivate” are lit. Under normal circumstances, the “Supply” and “smart-house” LEDs willbelitcontinuously,whereas the LED for “Communication” only blinks briefly when you push an associated BDF-WLS8 remote con- trol. The LED always lights up when you push a button. The LED indication provides confir- mation that the communication is successful. COMMUNICATION EXAMPLE smart-house bus TYPE SELECTION Supply Ordering no Battery (Not included)BDF-WLS8 1 2BH8-CTRLZx-xxx 1 2BH4-WBUA-230 DIMENSIONS / PUSH BOTTON Power smart-house RF Associate Disable Mode 50 mm 28 mm LED SW1SW2 I/O1 = SW1 I/O2 = SW2 I/O3 = SW3 I/O4 = SW4 I/O5 = SW5 I/O6 = SW6 PROGRAMMING I/O7 = SW7 I/O8 = SW8 Battery Programming with BGP-TPH-CAB The LED follows the activation of any of the 8 I/O. The LED is not programable. Specifications are subject to change without notice (05.09.2008) - A product of the CARLO GAVAZZI Group
All ratings we receive from the items we offer are real and verified. A small gesture, but a lot of value. That's why we thank you for that minute you invest in leaving us your opinion and qualification about the products, because it helps us to continue improving and to offer you a service of even higher quality.