Fault monitoring module with plug-in connection technology for evaluating and reporting group errors from the FM system and for monitoring the supply voltages. Error reporting via N/O contact. Push-in connection technology, standard configuration
The fault monitoring module with plug-in connection technology is used to evaluate and report group errors from the fault monitoring system of up to 115 connected MINI Analog Pro signal conditioners via the ME 6,2 TBUS-2 DIN rail connector (Order No.: 2869728). You can also monitor the supply voltages of MINI MCR-2-PTB(-PT) power terminals (Order No.: 2902066, 2902067). Drawing off the supply is also possible. The error is reported via an N/C contact. The error reporting module supports NFC communication.
Ambient temperature (operation)
-40 °C ... 70 °C
Ambient temperature (storage/transport)
-40 °C ... 85 °C
Degree of protection
Description of the input
Voltage input for redundancy monitoring
Number of inputs
Voltage input signal
9.9 V DC ... 30 V DC
Number of outputs
Voltage output signal
9.6 V DC ... 29.7 V DC
Max. output current
Maximum switching voltage
30 V DC
Max. switching current
Supply voltage range
12 V DC ... 24 V DC -20 % ... +25 % (The DIN rail bus connector (ME 6,2 TBUS-2 1,5/5-ST-3,81 GN, Order No. 2869728) can be used to bridge the supply voltage. It can be snapped onto a 35 mm DIN rail according to EN 60715))
Max. current consumption
< 16 mA (at 24 V DC)
< 410 mW (at 24 V DC)
Single conductor/terminal point, solid, with ferrule, min.
Single conductor/terminal point, solid, with ferrule, max.
Single conductor/terminal point, solid, without ferrule, min.
Single conductor/terminal point, solid, without ferrule, max.
Conductor cross section flexible min.
Conductor cross section flexible max.
Min. AWG conductor cross section, flexible
Max. AWG conductor cross section, flexible
Maximum temperature coefficient
< 0.01 %/K
1500 V AC (50 Hz, 1 min.)
Yellow LED (switching output)
Basic insulation according to EN 61010
Rated insulation voltage
50 V AC/DC (effective)
Test voltage input/output
1.5 kV AC (50 Hz, 1 min.)
Conformance with EMC Directive 2004/108/EC
EN 61000-6-2 When being exposed to interference, there may be minimal deviations.
Ex II 3 G Ex nA IIC T4 Gc X
UL, USA / Canada
UL 508 Listed
Class I, Div. 2, Groups A, B, C, D T6
Class I, Zone 2, Group IIC T6
Certificate of classification
DNV GL 14445-15HH
PDF of Fault monitoring module with plug-in connection technology for eva - PHOENIX CONTACT - MINI MCR-2-FM-RC-PT - 2904508