For use with
Type E starters do not need an upstream protective device.
For use in Canada, the PKZM0/PKZM4 must be fitted with an AK-PKZ0.
Service factor (SF)
Set value Ir on the current scale, depending on the load factor
SF = 1.15 ￫ Ir = 1 x In mot
SF = 1 ￫ Ir = 0.9 x In mot
Can be combined with three-phase commoning link B3…PKZ4.
Iu = 120 A.
For surface-mounting type-E starters.