Output Module BH4-RE16A8-230 8-channel receiver Relay load: 16 A Module load: 32 A (16 A per relay) Galvanically separated SPST relay outputs H4-housing For mounting on DIN-rail (EN 50022) LED-indications for supply, smart-house carrier and outputs AC power supply Address coding by BGP-COD-BAT OUTPUT SPECIFICATIONS Outputs8 SPST relays Contact ratings (AgSn02)µ (micro gap) Resistive loads AC1 16 A Mechanical lifetime 5x106 operations Electrical lifetime 1x105 operations/250 V, 12 A Minimum load 100 mA/12 V Operating frequency60 operations/min. Dielectric voltage Outputs – smart-house≥ 4 kVAC (rms) Response time≤ 1 pulse train SUPPLY SPECIFICATIONS Power Supply Overvoltage cat. III (IEC 60664) Rated operational voltage Through term. 21 & 22230 VAC, +/- 10% (IEC 60038) Frequency45 to 65 Hz Rated operational power Typ. 2,5 VA Power dissipation≤ 4 W Rated impulse withstand volt.4 kV Dielectric voltage Supply – smart-house≤4 kVAC (rms) Supply – Outputs≥2 kVAC (rms) GENERAL SPECIFICATIONS Fail polarity state delay Upon loss of smart-house carrier ≤ 20 ms Power ON delay typ. 2sIndication for: Supply ONLED, Green smart-house carrierLED, Yellow Output ONLED, red (one per output) Environment Degree of protectionIP 20 Pollution degree 3 (IEC 60664) Operating temperature -5 to +50°C (+23° to +122°F) MODE OF OPERATION Storage temperature -50 to +85°C (-58° to +185°F) Humidity (non-condensing)20 to 80% Mechanical resistance Shock5 G (11ms) Vibration2 G (6 to 55Hz) Housing H4-housing Weight 400 g TYPE SELECTION 8-channel receiver with 8 nor- mally open contact outputs. Each output is coded by means of the code programmer BGP-COD- BAT. For changing the default set- ting, please refer to the datasheet on BGP-COD-BAT. The outputs are normally OFF. When a transmitter coded to the selected channel is activated, the output turns ON and remains ON until the respective channel becomes deactivated. The default setting is such that upon loss of smart-house carrier all the out- puts go OFF. Note: At delivery some of the relays might be ON due to trans- portation bumps. To be sure that the relays are OFF, connect the module to power and smart- house and transmit on channels A1-8 once. Note: Due to the construction with bistable relays, the module is intended for heating and light control only. SupplyOrdering no. 230 VAC BH4-RE16A8-230 Specifications are subject to change without notice (05.11.2009) - A product of the CARLO GAVAZZI Group
All ratings we receive from the items we offer are real and verified. A small gesture, but a lot of value. That's why we thank you for that minute you invest in leaving us your opinion and qualification about the products, because it helps us to continue improving and to offer you a service of even higher quality.