Monitoring Relays Surge Arresters forAC systems Type DSF A/P • Type 2 (class C) according to EN61643-11 (VDE 0675, part 6-11) • Approved UL1449 3rd Edition • Complies with IEC-61643-1, UTE C 61-740-51 • Do not require backup fuse up to 200kArms (UL 1449 3rdEd.) • Innovative tecnology to prevent dangerous failures in case of temporary overvoltages • Suitable for unstable networks where sustainend over- voltages may persist for some minutes or longer • Plug-in cartridges • Optical indication of exhausted cartridges (red window) • Voltage-free contact, for remote function monitoring • Including thermal and dynamic separating device • Assembled unit ready for mounting • Marked connections • For DIN-rail mounting Product Description Ordering Key DSF 52 C A 277 DSF A/P are Type 2 (Class C) surge arresters according to EN 61643-11 (VDE 0675, part 6-11) and UL1449 3rd edition suitable for protect- ingAC systemsfromtran- sient overvoltage due to both indirect atmospheric discharges and switching actions. It is available for both single and three phase AC lines, TN-S and TN-C. The control windows (no/red indication) and the contact allow both a local and a remote monitoring of the status of the plug-in car- tridges,warning the opera- tor about the need to promptly replacethecar- tridges themselves. These surge protecting devices are Tipe II hence suitable for installation in main distributioncabinet, or secondarydistribution board, in installations with- outexternal LPS (Lightning Protection System) or where thedistance between the LPS elements and the solar panel frames is >50m. Thesedevicesdonot require any external backup fuse thus saving space and cost.Inaccordingto UL1449 3rd Ed. and UTE C 61-740-51 DSF and canbe installed on a DIN-rail in any commercially available dis- tribution box. Description Code Mounting DIN-rail D Function Surge arrestersS Type Type 2 (class C) “Fuseless” F Cartridge dimensions 17.5 mm5 Configuration Single pole1 Two poles (2+0)2 Three poles (3+0)3 4 poles (4+0) 4 Contact None X 1 (relay) C Network AC 1 phase A AC 3 phases P MCOV (AC) 150 VAC150 300 VAC277 385 VAC385 460 VAC 440 550 VAC 550 750 VAC 750 No backup-fuse tecnology Long duration overvoltage path The arrester is activated in the event of electric power system failure. The voltages are much lower than transient voltages butsubstantially more destructive. The system is composed of a current limitera and a varistor. In the event of increased voltage level the current limiter circuit lim- its the current through the varistor. When the normal condition is re-established (rat- ed line voltage), the surge arrester contin- ues to perform its normal function. Transient(short duration) overvoltage path The arrester is activated at the occurence of instantaneous high voltage surges last- ing only a few microseconds. Such condi- tion states are experienced at switching b operations and atmospheric discharges. The system is composed of a gas tube surge arrester and a varistor. Both compo- c nents have a very short response time which is reflected in a low protective resid- ual voltage level. This provides an efficient d protection of sensitive electronic devices. a) Current limiterb) Gas tubec) Thermal disconnectord) Varistor 1 Specifications are subject to change without notice. Pictures are just an example. For special features and/or customization, please ask to our sales network. REV0 100713
Todas las valoraciones que recibimos de los artículos que ofrecemos son reales y están verificadas. Un pequeño gesto, pero de mucho valor. Por eso, te agradecemos ese minuto que inviertes en dejarnos tu opinión y calificación sobre los productos, porque nos ayuda a seguir mejorando y a ofrecerte un servicio de todavía mayor calidad.