|Accessories, diagnostics & communication|
For measuring current, voltage, power, and energy.
In addition, the module requires three current transformers and three voltage taps wired externally. X/5A standard current transformers rated for up to 6,300 A are suitable.
230 VAC power supply
2 configurable outputs (S0 pulse, alarm, etc.)
RS-485 Modbus port (slave)
The total energy consumption value will be stored in retentive memory on the module.
BreakerVisu displays (NZM-XMC-MDISP...) can be used for visualization and logging purposes.
Number of poles
For use with
Rated operating frequency
|AC 50/60 Hz|
The minimum clearances relative to the NZM circuit-breaker need to be maintained for installation.
The module can be installed on the input or outgoer side, as well as on a top hat DIN rail.
The Eaton Modbus Configurator (www.eaton.eu) can be used to set up the module.
Cannot be combined with NZM-XMC-DISP display device.